| Zibo Bangyude Water Supply Equipment Co., Ltd. Tel: 0533-5760123 |
Company Fax: 0533-5760123
Official Website: jiccquao.com
Phone: 13335210119 (Manager Meng)
18953368321 (Manager Sun)
Company Address: Kunlun Town, Zichuan District, Zibo City
| 一定牛彩票网 >> Article List >> Details |
| Working principle of fire gas pressure equipment |
| 2016/8/4 14:50:23 |
| In the process of daily use and maintenance of fire gas top pressure equipment, do you find a problem, it not only has certain advantages in use and characteristics, its main application advantage is still its working principle Now, when we are working, we must briefly understand how it works. For details, let us briefly understand it from the following introduction. |
The fire-fighting air pressure water tank in the fire-fighting gas pressure equipment is a water storage component, and its minimum effective water volume is 3m3. The air pressure water tanks are all air-filled air pressure water tanks. This type of equipment relies on large air pressure water tanks to provide 10 minutes of initial fire fighting water consumption. There is no fire pump set, only the fire pressure stabilization pump set. The main difference is that the gas pressure equipment uses high-pressure gas cylinders to store the power gas source for fire protection work. The power gas source is separated from the air pressure water tank. When the fire control instruction is reached, the top pressure system is started to input the air pressure water tank to meet the fire work pressure. The gas is replaced and discharged from the fire fighting water in the tank, and the fire fighting water is supplied to the fire fighting parts at a constant pressure.
The daily fire-fighting gas pressure equipment sends water to the pipe network and the air pressure water tank during work. When the liquid level in the air pressure water tank reaches the upper limit of the set value, the make-up pump stops working. When the pressure is insufficient, the gas supply system works, and when the pressure rises to the upper limit of the pressure regulation, gas supply is stopped. Usually the system leaks cause the pressure of the pipe network to drop. The liquid level controller controls the pressure-stabilizing pump to start the water supply; the system gas volume is lacking; the pressure controller controls the gas supply system (air compressor) to start and stop the gas supply; To gas-liquid equilibrium, pressure and liquid level interlock. When a fire occurs, the fire signal is input, and the gas pressure system works to release the power source of pressure. It is evenly filled into the air pressure water tank and the water is pumped into the fire pipe network. The fire water is provided to the pipe network for no less than 10 minutes.
We can find out from the above that, in fact, there are certain requirements when the fire gas top pressure equipment is working, so we need everyone to pay special attention when using it, and it can be true in use and maintenance. Reasonable use, and everyone can find and solve problems in a timely manner.